Edition 1: Compressed Air Leaks
Cost Reduction Opportunities in Compressed Air Systems
Leaks are a Source of Waste.
Leaks can be a significant source of wasted energy in a compressed air system, sometimes wasting 20 – 30 % of a compressor’s output. A Typical plant that has not been well maintained will likely have a leak rate equal to 20-30% of total compressed air production capacity or more. On the other hand, Proactive Leak detection and repair can reduce leaks to less than 5 – 10 % of Compressor Output.
In addition to being a source of wasted energy, leaks can also contribute to other operating losses. Leaks,
Cause a drop in system pressure, which can make machines function less efficiently, adversely affecting production.
Shorten the life of almost all supply system equipment including the compressor itself by forcing the equipment to operate more frequently.
Cause increased running time, which can also lead to additional maintenance requirements and increased unscheduled downtime and
Can lead to adding unnecessary compressor capacity.
Table.1 – Estimation of Leakage Losses in Textile Spinning Mills
Since Air Leaks are almost impossible to see, other methods must be used to locate them. The Best way to detect leaks is to use an very Accurate and Advanced ultrasonic acoustic detector, which can filter the background noises and recognise the high frequency associated with air leaks. These instruments consist of directional microphones, amplifiers, audio filters and usually have visual indicators and earphones to detect leaks. Since Ultrasound is directional in transmission, the signal is loudest at its source. By Generally scanning around a test area, it is possible to very quickly locate a leak site and find its location. For this reason, ultrasonic leak detection is not only fast, it is also very accurate.
Establishing an Effective Leakage Management Program is a Key step in managing your compressed air system. With a Leak Tag Program, the leak is identified, tagged and logged for a repair at a later time. Documentation should include the location of leak, type of leak and the estimated cost of leak. The Documentation should be compatible with the Predictive Maintenance Program of the facility. Further Documenting the repairs and the type of leaks can also indicate equipment that is a reoccurring problem. When this occurs, the process should be looked at for a root cause and permanent solution should be developed to stop the reoccurring air leaks.
Tracking & Verification:
By Comparing Before and After, the effectiveness of the program and the savings can be determined. Air Leaks Continue to occur so the program has to be ongoing. Periodic reviews should be done on the system and the process repeated as necessary to maintain system efficiency.
A Good Compressed Air System Leak Management Program is very important in maintaining the efficiency, reliability, stability and cost effectiveness of any compressed air system.
Managing Director – Asia Pacific,
Systel Energy Solutions (India) Pvt Ltd,